LED HID Replacement Bulbs
LED replacements for high watt HID lamps provide savings of up to 80% on energy costs and reduced maintenance with a 50,000 hour LED rated life. These LED lamps replicate the lighting performance of high-intensity discharge and metal halide bulbs. The LED lamps include UL Type A direct replacement and UL-Type B ballast bypass with line voltage wired to the socket. LED lamps are available to replace HID and metal halide bulbs in post top, wall pack, high/low bay, cobra head and industrial fixtures. If you have questions, please call one of our lighting specialists at 800.784.1998.
LED for HID Lamp Retrofit Options
Manufacturers of LED lamps designed to replace metal halide generally offer two installation options:
- UL Type A: Ballast Compatible
- UL Type B: Ballast Bypass with Line Voltage to the Socket
UL Type A Installation
For ease of installation and lower overall install expense, UL Type A lamp retrofits are the choice. Simply remove the metal halide lamp and install the LED.
However, some compromises are inherent in this type of installation. Because the lamps operate directly off the existing metal halide ballast, the efficacy of the LED lamp may be degraded by an inefficient ballast. In addition if the ballast is old, it may stop working long before the LED lamp. This will require an additional cost.
UL Type B Installation
An electrician is required to remove the existing ballast and re-wire line voltage directly to the socket. The advantages of this approach is eliminating compatibility issues with a ballast. This is the simplest total system with excellent LED efficacy. Disadvantages include the need to install a fuse to avoid injury if future maintenance staff reinstall metal halide lamps and the higher overall install cost compared to UL Type A.
Ultimately, the decision for which type of LED installation to use depends on an assessment of the existing ballast (is it relatively new and efficient or old and inefficient) and on the budget.